A deaerator is a device that is widely used for the removal of oxygen and other dissolved gases from the feedwater to steam-generating boilers. In particular, dissolved oxygen in boiler feedwaters will cause serious corrosion damage in steam systems by attaching to the walls of metal piping and other metallic equipment and forming oxides (rust). Water also combines with any dissolved carbon dioxide to form carbonic acid that causes further corrosion. Most deaerators are designed to remove oxygen down to levels of 7 ppb by weight (0.005 cm³/L) or less.
- The tray-type (also called the cascade-type) includes a vertical domed deaeration section mounted on top of a horizontal cylindrical vessel which serves as the deaerated boiler feedwater storage tank.
- The spray-type consists only of a horizontal (or vertical) cylindrical vessel which serves as both the deaeration section and the boiler feedwater storage tank.
Types of deaerators
There are many different horizontal and vertical deaerators available from a number of manufacturers, and the actual construction details will vary from one manufacturer to another. Figures 1 and 2 are representative schematic diagrams that depict each of the two major types of deaerators.
The typical horizontal tray-type deaerator in Figure 1 has a vertical domed deaeration section mounted above a horizontal boiler feedwater storage vessel. Boiler feedwater enters the vertical dearation section above the perforated trays and flows downward through the perforations. Low-pressure deaeration steam enters below the perforated trays and flows upward through the perforations. Some designs use various types of packing material, rather than perforated trays, to provide good contact and mixing between the steam and the boiler feed water.
The steam strips the dissolved gas from the boiler feedwater and exits via the vent at the top of the domed section. Some designs may include a vent condenser to trap and recover any water entrained in the vented gas. The vent line usually includes a valve and just enough steam is allowed to escape with the vented gases to provide a small and visible telltale plume of steam.
The deaerated water flows down into the horizontal storage vessel from where it is pumped to the steam generating boiler system. Low-pressure heating steam, which enters the horizontal vessel through a sparger pipe in the bottom of the vessel, is provided to keep the stored boiler feedwater warm. External insulation of the vessel is typically provided to minimize heat loss.
As shown in Figure 2, the typical spray-type deaerator is a horizontal vessel which has a preheating section (E) and a deaeration section (F). The two sections are separated by a baffle(C). Low-pressure steam enters the vessel through a sparger in the bottom of the vessel.
The boiler feedwater is sprayed into section (E) where it is preheated by the rising steam from the sparger. The purpose of the feedwater spray nozzle (A) and the preheat section is to heat the boiler feedwater to its saturation temperature to facilitate stripping out the dissolved gases in the following deaeration section.
The preheated feedwater then flows into the dearation section (F), where it is deaerated by the steam rising from the sparger system. The gases stripped out of the water exit via the vent at the top of the vessel. Again, some designs may include a vent condenser to trap and recover any water entrained in the vented gas. Also again, the vent line usually includes a valve and just enough steam is allowed to escape with the vented gases to provide a small and visible telltale plume of steam
The deaerated boiler feedwater is pumped from the bottom of the vessel to the steam generating boiler system.
The deaerators in the steam generating systems of most thermal power plants use low pressure steam obtained from an extraction point in their steam turbine system. However, the steam generators in many large industrial facilities such as petroleum refineries may use whatever low-pressure steam is available.
Oxygen scavenging chemicals are very often added to the deaerated boiler feedwater to remove any last traces of oxygen that were not removed by the deaerator. The most commonly used oxygen scavenger is sodium sulfite (Na2SO3). It is very effective and rapidly reacts with traces of oxygen to form sodium sulfate (Na2SO4) which is non-scaling. Another widely used oxygen scavenger is hydrazine (N2H4).
- Air preheater
- Feedwater heater
- Fossil fuel power plant
- Thermal power station
- ^ a b Pressurized deaerators
- ^ Deaerator Presentation
- ^ Spray-type Deaerator Operating Principal
- ^ Robert Thurston Kent (Editor in Chief) (1936). Kents’ Mechanical Engineers’ Handbook (Eleventh edition (Two volumes) ed.). John Wiley & Sons (Wiley Engineering Handbook Series).
- ^ Babcock & Wilcox Co. (2005). Steam: Its Generation and Use (41st edition ed.). ISBN 0-9634570-0-4.
- ^ Thomas C. Elliott, Kao Chen, Robert Swanekamp (coauthors) (1997). Standard Handbook of Powerplant Engineering (2nd edition ed.). McGraw-Hill Professional. ISBN 0-07-019435-1.
Wikimedia Foundation. 2010.
Look at other dictionaries:
deaerator — deaeratorius statusas T sritis Energetika apibrėžtis Aparatas dujoms (deguoniui, anglies dioksidui) iš vandens šalinti. Deaeratoriai įrengiami šiluminėse elektrinėse ir katilinėse į garo generatorius ir į šilumos tinklus tiekiamam vandeniui… … Aiškinamasis šiluminės ir branduolinės technikos terminų žodynas
deaerator — noun see deaerate … New Collegiate Dictionary
deaerator — de·aerator … English syllables
deaerator — noun see deaerate … Useful english dictionary
deaerator tray/chamber — A container in which the air bubbles are separated from the returned oil before it is recirculated into the lubrication system of a gas turbine engine. Any air in the oil is allowed to escape while the oil is in the tray. It is a type of air oil… … Aviation dictionary
Thermal power station — Republika Power Plant, a thermal power station in Pernik, Bulgaria … Wikipedia
Chernobyl disaster — This article is about the 1986 nuclear plant accident in Ukraine. For other uses, see Chernobyl (disambiguation). Chernobyl disaster … Wikipedia
ДЕАЭРАТОР — аппарат для удаления из воды растворённых кислорода и двуокиси углерода, вызывающих коррозию оборудования (Болгарский язык; Български) деаератор; обезвъздушител (Чешский язык; Čeština) odvzdušovací zařízení; deaerátor (Немецкий язык; Deutsch)… … Строительный словарь
VVER — The VVER (From (Russian: Водо водяной энергетический реактор , transliterates as Vodo Vodyanoi Energetichesky Reactor , translates as Water Water Energetic Reactor , WWER. Water water stands for coolant and moderator.) is a series of pressurised… … Wikipedia
oil separator — A device used to separate oil from the discharged air from the crankcase vent. It consists of a series of baffles over which discharged air from the vent passes. The oil sticks to the baffles and drains to the bottom of the separator housing and… … Aviation dictionary