- Pressurized water reactor
Pressurized water reactor (PWRs) (also
VVERif of Russian design) are generation II nuclear power reactors that use ordinary waterunder high pressure ( superheated water) as coolant and neutron moderator. The primary coolant loop is kept under high pressure to prevent the water from reaching film boiling, hence the name. PWRs are the most common type of power producing reactor and are widely used all over the world. More than 230 of them are in use to generate electric power, and several hundred more for naval propulsion. They were originally designed at the Oak Ridge National Laboratoryfor use as a nuclear submarinepower plant. Follow-on work was conducted by Bettis Atomic Power Laboratory. [ cite web
title= Rickover: Setting the Nuclear Navy's Course
author= |last= |first= |authorlink= |coauthors=
date= |year= |month= | work= ORNL Review | publisher=
Oak Ridge National Laboratory, U.S. Dept. of Energy
accessdate= 2008-05-21 ]
The reactors are used in
nuclear power plantsto produce nuclear powerfrom nuclear fuel.
A PWR works because the
nuclear fuelin the "reactor vessel" is engaged in a chain reaction, which produces heat, heating the water in the primary coolant loop by thermal conduction through the fuel cladding. (The primary coolant loop is shown in the schematic as a red dashed line.) The hot water is pumped into a heat exchangercalled "steam generator", which allows the primary coolant to heat up and boil the secondary coolant (shown as the loop "steam generator" → "turbine" → "condenser"). The transfer of heat is accomplished without mixing the two fluids. This is desirable, since the primary coolant is necessarily radioactive. The steam formed in the steam generator is allowed to flow through a steam turbine, and the energy extracted by the turbine is used to drive an electric generator. Other uses for the steam from a PWR include:
*In nuclear ships and submarines, the steam is fed through a steam turbine connected to a set of speed reduction
gearsto a shaft used for propulsion
*Direct mechanical action by expansion of the steam for things like a steam-powered
District heatingby the steamIn a nuclear power station, the steam is fed through a steam turbine which drives a generator connected to the electric grid for distribution, as shown above. After passing through the turbine the secondary coolant (water-steam mixture) is cooled down and condensed in a " condenser" before being fed into the steam generator again. This converts the steam to a liquid so that it can be pumped back into the high pressure steam generator.
Two things are characteristic for the pressurized water reactor (PWR) when compared with other reactor types:
* In a PWR, there are two separate coolant loops (primary and secondary), which are both filled with demineralized/deionized water. A
boiling water reactor, by contrast, has only one coolant loop, while more exotic designs such as breeder reactors use substances other than water for the task (e.g. sodium in its liquid state).
* The pressure in the primary coolant loop is typically 15–16 Megapascal, which is notably higher than in other
nuclear reactors, and nearly twice that of a Boiling water reactor(BWR). As an effect of this, only localized boiling occurs and will recondense promptly in the bulk fluid. By contrast, in a boiling water reactorthe primary coolant is designed to boil.
Heat from small PWRs has been used for heating in polar regions in the
Army Nuclear Power Program.
PWR reactor design
Light wateris used as the primary coolant in a PWR. It enters the bottom of the reactor core at about 275 °C (530 °F) and is heated as it flows upwards through the reactor core to a temperature of about 315 °C (600 °F). The water remains liquid despite the high temperature due to the high pressure in the primary coolant loop, usually around 155 bar (15 MPa 150 atm, 2,250 psig). Pressure in the primary circuit is maintained by a Pressuriser, a separate vessel that is connected to the primary circuit and partially filled with water which is heated to the saturation temperature (boiling point) for the desired pressure by submerged electrical heaters. To achieve a pressure of 155 bar, the pressuriser temperature is maintained at 345 °C, which gives a subcooling margin (the difference between the pressuriser temperature and the highest temperature in the reactor core) of 30 °C. To achieve maximum heat transfer, the primary circuit temperature, pressure and flow rate are arranged such that subcooled nucleate boilingtakes place as the coolant passes over the nuclear fuel rods.
The coolant is pumped around the primary circuit by powerful pumps, which can consume up to 6 MWe each. After picking up heat as it passes through the reactor core, the primary coolant gives up heat in a steam generator to water in a lower pressure secondary circuit, evaporating the secondary coolant to saturated steam — in most designs 6.2 MPa (60 atm, 900
psia), 275 °C (530 °F) — for use in the steam turbine. The cooled primary coolant is then pumped back to the reactor to be heated again.
Although coolant flow rate in commercial PWRs is constant, it is not in nuclear reactors used on U.S. Navy ships.
Pressurized water reactors, like
thermal reactordesigns, require the fast fission neutrons in the reactor to be slowed down (a process called moderation) in order to sustain its chain reaction. In PWRs the coolant water is used as a moderator by letting the neutrons undergo multiple collisions with light hydrogen atoms in the water, losing speed in the process. This "moderating" of neutrons will happen more often when the water is more dense (more collisions will occur). The use of water as a moderator is an important safety feature of PWRs, as any increase in temperature causes the water to expand and become less dense; thereby reducing the extent to which neutrons are slowed down and hence reducing the reactivity in the reactor. Therefore, if reactivity increases beyond normal, the reduced moderation of neutrons will cause the chain reaction to slow down, producing less heat. This property, known as the negative temperature coefficientof reactivity, makes PWR reactors very stable.
In contrast, the
RBMKreactor design used at Chernobyl, which uses graphite instead of water as the moderator and uses boiling water as the coolant, has a high positive coefficient of reactivity, that increases heat generation when coolant water temperatures increase. This makes the RBMK design less stable than pressurized water reactors. In addition to its property of slowing down neutrons when serving as a moderator, water also has a property of absorbing neutrons, albeit to a lessor degree. When the coolant water temperature increases, the boiling increases, which creates voids. Thus there is less water to absorb thermal neutrons that have already been slowed down by the graphite moderator, causing an increase in reactivity. This property is called the void coefficientof reactivity, and in an RBMK reactor like Chernobyl, the void coefficient is positive, and fairly large, causing rapid transients. This design characteristic of the RBMK reactor is generally seen as one of several causes of the Chernobyl accident. [ cite web
title= Achievement of Negative Reactivity Feedback Effects
author= |last= |first= |authorlink= |coauthors=
date= |year= |month= | format=
Massachusetts Institute of Technology
accessdate= 2008-05-21 ]
CANDU reactors, (which use heavy water as a coolant and neutron moderator) also have a positive void coefficient, though it is not as large as that of an RBMK like Chernobyl; these reactors are designed with a number of safety systems not found in an RBMK, which are designed to handle or react to this as needed.
After enrichment the uranium dioxide (UO2) powder is fired in a high-temperature,
sinteringfurnace to create hard, ceramic pellets of enriched uranium dioxide. The cylindrical pellets are then clad in a corrosion-resistant zirconium metal alloy (Zircaloy) which are backfilled with helium to aid heat conduction and detect leakages. Zircaloyis chosen because of its mechanical properties and its low absorption cross section. [cite web
title= Uses of Zirconium Alloys in Fusion Applications
last= Forty | first= C.B.A. | coauthors= P.J. Karditsas
date= |year= |month= |format= |work=
publisher= EURATOM/UKAEA Fusion Association, Culham Science Centre
accessdate= 2008-05-21 ] The finished fuel rods are grouped in fuel assemblies, called fuel bundles, that are then used to build the core of the reactor. As a safety measure PWR designs do not contain enough fissile uranium to sustain a
prompt criticalchain reaction (i.e, substained only by prompt neutrons). Avoiding prompt criticality is important as a prompt critical chain reaction could very rapidly produce enough energy to damage or even melt the reactor. A typical PWR has fuel assemblies of 200 to 300 rods each, and a large reactor would have about 150–250 such assemblies with 80–100 tonnes of uranium in all. Generally, the fuel bundles consist of fuel rods bundled 14 × 14 to 17 × 17. A PWR produces on the order of 900 to 1,500 MWe. PWR fuel bundles are about 4 meters in length.
Refuelings for most commercial PWRs is on an 18–24 month cycle. Approximately one third of the core is replaced each refueling.
Generally, reactor power can be viewed as following steam (turbine) demand due to the reactivity feedback of the temperature change caused by increased or decreased steam flow. Boron and control rods are used to maintain primary system temperature at the desired point. In order to decrease power, the operator throttles shut turbine inlet valves. This would result in less steam being drawn from the steam generators. This results in the primary loop increasing in temperature. The higher temperature causes the reactor to fission less and decrease in power. The operator could then add boric acid and/or insert control rods to decrease temperature to the desired point.
Reactivity adjustments to maintain 100% power as the fuel is burned up in most commercial PWRs is normally controlled by varying the concentration of
boric aciddissolved in the primary reactor coolant. The boron readily absorbs neutrons and increasing or decreasing its concentration in the reactor coolant will therefore affect the neutron activity correspondingly. An entire control system involving high pressure pumps (usually called the charging and letdown system) is required to remove water from the high pressure primary loop and re-inject the water back in with differing concentrations of boric acid. The reactor control rods, inserted through the top directly into the fuel bundles, are moved for the following reasons:
1. To enable reactor start up.
2. To shut down the reactor.
3. To compensate for
4. To compensate for
In contrast, BWRs have no boron in the reactor coolant and control the reactor power by adjusting the reactor coolant flow rate.
Due to design and fuel enrichment differences, naval nuclear reactors do not use boric acid.
*PWR reactors are very stable due to their tendency to produce less power as temperatures increase; this makes the reactor easier to operate from a stability standpoint.
*PWR reactors can be operated with a core containing less fissile material than is required for them to go
prompt critical. This significantly reduces the chance that the reactor will run out of control and makes PWR designs relatively safe from criticality accidents.
*Because PWR reactors use enriched uranium as fuel, they can use ordinary water as a moderator rather than the much more expensive
heavy wateras used in a pressurized heavy water reactor.
*PWR turbine cycle loop is separate from the primary loop, so the water in the secondary loop is not contaminated by radioactive materials.
*The coolant water must be highly pressurized to remain liquid at high temperatures. This requires high strength piping and a heavy pressure vessel and hence increases construction costs. The higher pressure can increase the consequences of a
loss of coolant accident.
*Most pressurized water reactors cannot be refueled while operating. This decreases the availability of the reactor- it has to go offline for comparably long periods of time (some weeks).
*The high temperature water coolant with
boric aciddissolved in it is corrosive to carbon steel (but not stainless steel), this can cause radioactive corrosion products to circulate in the primary coolant loop. This not only limits the lifetime of the reactor, but the systems that filter out the corrosion products and adjust the boric acid concentration add significantly to the overall cost of the reactor and radiation exposure. Occasionally, this has resulted in severe corrosion to control rod drive mechanisms when the boric acid solution leaked through the seal between the mechanism itself and the primary system. [
title = Davis-Besse: The Reactor with a Hole in its Head
booktitle = UCS -- Aging Nuclear Plants
publisher = [http://www.ucsusa.org/ Union of Concerned Scientists]
url = http://www.ucsusa.org/assets/documents/clean_energy/ACFNx8tzc.pdf
accessdate = 2008-07-01
cite press release
title = NRC: Bulletin 82-02: Degradation of Threaded Fasteners in the Reactor Coolant Pressure Boundary of PWR Plants
Nuclear Regulatory Commission
date = June 2, 1982
url = http://www.nrc.gov/reading-rm/doc-collections/gen-comm/bulletins/1982/bl82002.html
accessdate = 2008-07-01
*Natural uranium is only 0.7% Uranium-235, the isotope necessary for thermal reactors. This makes it necessary to enrich the uranium fuel, which increases the costs of fuel production. If
heavy wateris used it is possible to operate the reactor with natural uranium, but the production of heavy water requires large amounts of energy and is hence expensive.
*Because water acts as a neutron moderator it is not possible to build a
fast neutron reactorwith a PWR design. A reduced moderation water reactormay however achieve breeding ratiogreater than unity, though these have disadvantages of their own.
List of PWR reactors
Boiling Water Reactor
Next generation designs
European Pressurized Reactor(EPR)
* Westinghouse Advanced Passive 1000 (AP1000)
Wikimedia Foundation. 2010.
Look at other dictionaries:
pressurized water reactor — noun a nuclear reactor that uses water as a coolant and moderator; the steam produced can drive a steam turbine • Syn: ↑PWR • Hypernyms: ↑water cooled reactor * * * pressurized water reactor noun A nuclear reactor using water cooling at a… … Useful english dictionary
Pressurized Water Reactor — Réacteur à eau pressurisée Pour les articles homonymes, voir REP et PWR. Schéma d une tranche nucléaire disposant d un REP Le réacte … Wikipédia en Français
pressurized water reactor — suslėgtu vandeniu aušinamas reaktorius statusas T sritis fizika atitikmenys: angl. pressurized water reactor vok. druckwassergekühlter Reaktor, m; Druckwasserreaktor, m rus. реактор, охлаждаемый водой под давлением, m pranc. pile à l’eau… … Fizikos terminų žodynas
pressurized water reactor — suslėgtojo vandens reaktorius statusas T sritis Energetika apibrėžtis Branduolinis reaktorius, kurio lėtiklis ir šilumnešis yra suslėgtas vanduo. atitikmenys: angl. pressurized water reactor vok. Druckwasserreaktor, m rus. реактор с водой под… … Aiškinamasis šiluminės ir branduolinės technikos terminų žodynas
Pressurized-water reactor — (PWR) A nuclear reactor in which heat is transferred from the core to a heat exchanger via water kept under high pressure, so that high temperatures can be maintained in the primary system without boiling the water. Steam is generated in a… … Energy terms
Pressurized water reactor — (PWR) A nuclear power unit cooled by water that is pressurized to keep it from boiling when it reaches high temperatures. California Energy Comission. Dictionary of Energy Terms … Energy terms
pressurized-water reactor — noun a nuclear reactor in which the coolant and moderator is water under high pressure … English new terms dictionary
pressurized-water reactor — … Useful english dictionary
European Pressurized Water Reactor — Schaubild eines EPR Der Europäische Druckwasserreaktor (engl. European Pressurized Water Reactor, kurz EPR) ist ein neuer Kernreaktortyp basierend auf dem Druckwasserreaktor. Der EPR wurde in der zweiten Hälfte der 1990er Jahre von den… … Deutsch Wikipedia
Pressurized Heavy Water Reactor — Schema eines CANDU Reaktors Brennstoffbündel eines CANDU Reaktors Ein CANDU Reaktor (CANada Deuterium Uranium) ist ein Schwerwasserreaktor, der von der … Deutsch Wikipedia